Trust The Comfort Of Your Oak Ridge, NJ Home To The Best In HVAC Service
If you live in Northern New Jersey, then you already know that for decades Climate Plus has been the go-to HVAC service provider. Whether it's HVAC maintenance or AC repair, Climate Plus has always had our Oak Ridge customers' best interests at heart. Not only that, but we also specialize in installation, oil to gas conversions on furnaces and heat pumps when needed. If you're looking for ways to improve your indoor air quality, we've got you covered there too! We offer a variety of tools including UV lights, humidifiers and dehumidifiers, and the best air filters around so you can keep your home nice and comfortable all day long. So don't delay; next time you need HVAC services or AC repair call (973) 838-3200 so you can rest easy knowing the air inside your home is as clean and cozy as it's ever been!
The cost of AC repair can vary depending on the specific issue and the geographic location. Minor repairs like a refrigerant recharge or replacing a capacitor can cost between $100 to $500. More significant repairs, like fixing a compressor or replacing a coil, can cost $1,000 to $2,500 or more. The cost of repairs may also depend on the age and condition of the AC unit. It's important to obtain a written estimate from a licensed HVAC contractor before any work is done to ensure transparency and accuracy of the cost.
There can be a variety of reasons why a home AC unit stops working all of a sudden. Some common causes include a tripped circuit breaker, a dirty air filter, a malfunctioning thermostat, a faulty capacitor, a refrigerant leak, or a frozen evaporator coil. It's also possible that there is a problem with the compressor or the fan motor. It's best to have a licensed HVAC contractor diagnose the issue to determine the cause and provide the appropriate repair. Regular maintenance can also help prevent sudden breakdowns of AC units.
AC units should be serviced at least once a year, preferably before the start of the cooling season. This regular maintenance can help to ensure that the unit is running efficiently and effectively, and can also help to identify any potential problems before they become major issues. During a maintenance visit, a licensed HVAC contractor will typically inspect the unit, clean the coils and filters, lubricate moving parts, check refrigerant levels, and test the electrical components. Regular servicing can also extend the life of the AC unit and improve indoor air quality.
Hear It From Our Greatest Cheerleaders - Our Customers!
Our customer reviews speak for themselves - Climate Plus takes the cake when it comes to quality HVAC services in New Jersey. With over hundreds of customer recommendations going back to our earliest days, our commitment to honest, dependable work is unmatched. Check out all of our customer reviews below and find out why we're a degree above the rest. When you're ready to get serious about your HVAC services, why not go with a team that's tried and true? Give us a call at Climate Plus and experience honest service with a side of Jersey humor!
for Oak Ridge, NJ
Our Reviews by City
HVAC Maintenance near Greenwood Dr. Came out to perform springtime maintenance on a client's York HVAC unit. Conducted a diagnostic examination of the unit to guarantee its reliable operation for the client all year round. Verified refrigerant levels, swapped out filters, and unclogged the condensate drain line. Everything seems to be in good working order with the unit.
Water Heater Replacement Services near Overlook Dr. Arrived at the client's home to replace their old water heater with a new Rheem tankless water heater. Successfully installed the new unit into the home to provide the client with a reliable option for their hot water needs.
Springtime HVAC Maintenance near Wood Duck Rd. Arrived at the client's home for annual springtime HVAC maintenance services. Performed a full system diagnostic maintenance review on the home’s HVAC system to maintain optimal performance throughout the season change. Cleared condensate drain lines. Replaced filters. No other issues to document.